FLOW SURVEYS DELIVER KEY INFILTRATION ANALYSIS AND DATA FOR EXPANDING HOLIDAY PARK
A leisure industry business that owns a large caravan & holiday park in Wales that attracts more than 200,000 visitors and employs hundreds of people, contracted Detectronic to implement two flow surveys at the site.
The client is looking to invest up to £12.5 million to further enhance the park with a series of developments, and it was imperative that they gain an indepth understanding of the hydrology of the site to inform planned infrastructure works.
“Following a number of discussions and site visits, we devised and implemented the first targeted flow survey in October 2017 over a two-week period,” explains Oliver Harrison, sales engineer for Detectronic.
“The purpose of this initial survey was to deliver inflow and infiltration analysis and our team installed MSFM flow monitors and two rain-gauges at nine strategic locations across the site to gather data.
“Each of the monitors gave us very specific data relating to depth, velocity and rainfall impact at each location which, in turn, provided diurnal patterns and enabled our data centre analysts to provide a full report highlighting a number of issues that might affect the development.”
The report recorded significant volume and percentage of inflow and infiltration into the foul sewer network at several of the monitored locations. It provided invaluable data to inform the development process including the effect of rainfall events on the site (with further flow measuring recommended at two locations) and potential blockages caused by fats, oils and greases (FOGs). It also led to the recommendation of regular cleansing in certain sections of the sewer, highlighted network infiltration close to railway lines as trains passing overhead had potentially loosened pipes and identified an issue originating from a pumping station downstream from the park.
Continues Oliver: “In order to assess the efficacy and success of the consequent remediation work, we were asked to implement a second inflow and infiltration analysis survey commencing in June 2018 and running for an eight-week period. For this survey we recommended and installed ten MSFM flow monitors, two rain-gauges and a pump run monitor at different locations within the holiday park.
“The second survey we implemented provided further key information and determined which parts of the catchment have problems. As such, an engineer visited these problematic areas to carry out repair works to fix broken pipes and misconnected/cross-connected gullies. This particular work has resulted in the reduction of inflow and infiltration (I&I) on site and we have been asked to deliver a further site survey to assess the value of this latest stage of works and inform any further improvements that could be made.”download case study